(1) the overall layout of the laboratory project conforms to the design requirements of the drawings and is reasonable and orderly;
(2) the materials and specifications of the lab furniture conform to the design requirements, and the quantities are in conformity with the list of the engineering plans, and there is a valid inspection certificate and a test report;
(3) furniture installation is correct, firm and tight, and the deviation shall be within the design standard control range. The components are tightly connected without any content exposed;
(4) the table (central platform and side platform) has smooth surface, uniform color and smooth and smooth edges. The cabinet body is firm, the cabinet body plate coating color is even, the sealing edge is tight. The door opened and closed freely, no abnormal sound. The flat surface is free from burrs, and the height adjusting buckle is flexible and effective. The back plate has tight edge and no deformation. Baseboard without load deformation. Adjusting feet is flexible and difficult to deform.
(5) the slideway of the test table is flexible and effective, with no paint shedding. The hinge, handle is bright, rust proof.
(6) the modification of electrical wiring is reasonable, orderly and safe. The socket is safe and effective, and the installation position is reasonable, without hindering the experimental operation.
(7) each joint of the reagent rack is tight and seamless; the board is smooth, the articles are not easy to slide, and the load is not deformed.
(8) the tank is resistant to acid and alkali corrosion, and it is tightly jointed with the experimental table. Traps unobstructed drainage is not easy to block. The tap valve is flexible and effective, no water leakage, no water outlet splash phenomenon. The door opened and closed freely, easy to repair and drainage pipeline.
(9) the cabinet is firmly installed, easy to use. The door opened and closed freely, the glass is not easy to fall off. The backboard is tightly connected with the cabinet body, and the height adjusting buckle of the plywood is flexible and effective.
(10) the platform is stable and shockproof, the surface of the table is free of sag, and the edge is smooth and smooth. The balance place can be adjusted independently and operated freely.
(11) the original structure has not been damaged during the installation of laboratory furniture.
This article by operation room decoration for you, our website is: http://www.sdyhrs.com, we will wholeheartedly enthusiasm for you to provide better service, you are welcome to visit!