With the construction and development of modern hospital, new and higher requirements are put forward for the daily maintenance and troubleshooting of air conditioning purification system.
Clean operating room decoration is the key department of the hospital, with high cleanliness and complex control. With the construction and development of modern hospital, new and higher requirements are put forward for the daily maintenance and troubleshooting of air conditioning purification system. This paper introduces several typical faults of air conditioning purification system in operating room, and puts forward corresponding treatment methods.
The purified air volume of operating room does not meet the requirements.
Air intake is an important index to measure the cleanliness of operating room. Mainly through the control panel control frequency converter, adjust the unit fan start stop and speed.
If the air intake does not meet the requirements, check whether the blower works normally. If it works normally, the air duct may be blocked due to too much dust in the primary or medium efficiency filter. Cleaning or changing the filter can eliminate the fault.
Operating room is a place with high cleanliness requirements, air conditioning control system is a complex control process. This requires us to understand the working principle of the system, as well as the normal working conditions and various parameters, and consider more observations.
You can solve this problem quickly and accurately. At the same time, in daily work, the equipment should be checked regularly, and the problems should be nipped in the bud to reduce the occurrence of equipment failure.