装修后的手术室不仅能很好地满足使用功能的要求，也为医护人员和患者营造了一个良好的医疗环境。整体要求包括 ICU 及手术室的准备区、隔离区和手术区三大区域，根据规模大小，按比例合理分割统筹考虑，包括房间设置、设施摆放、通道划分，医护人员与病员、家属之间的关系，要求有序。
After the decoration, the operation room can not only meet the requirements of the use of functions well, but also create a good medical environment for medical staff and patients. The overall requirements including ICU and operation room preparation area, the isolation zone and the operation area of three regions, according to the size, according to the proportion of reasonable division of the overall consideration, including room setting, facilities placed, channel division, the relationship between medical staff and patients, their families, the requirement of efficient and orderly.
Medical gas, water supply and drainage, distribution, insulation cabinet for insulation cabinet should be embedded design
The clean operating department must have oxygen, compressed air and negative pressure to attract three kinds of air and equipment. When necessary can also be provided with Nitrous Oxide (two nitrogen oxide or nitrous oxide), nitrogen, argon and air emissions waste gas recovery device. Medical gases must have a reserve of no less than three days. The medical gas terminal of the clean operation room must have a set of spare. The water supply system in the clean operating department should have two routes and should have a hot and cold water system at the same time. The water quality of the clean operating department must be in accordance with the standard of drinking water; the water removal of the brush hand should be carried out, and the storage of hot water should prevent the breeding of bacteria. The direct fire hydrant water supply system and the portable gas extinguisher should be set up in the clean operating department.
The clean operating department must provide a two way power supply that can automatically switch from the special line of the distribution center of its building. The electricity used in the clean operating room should be separated from the auxiliary room, and the trunk of each operation room must be laid alone. In addition to the design requirements, the total distribution load of the medical equipment and equipment in the clean operating room should not be less than 8kVA